- Live Motion Amplification®
- Calibrated Displacement Measurements
- Frequency Based Filtering
- Advanced Troubleshooting
AGL Loy Yang - Power
Latrobe Valley, Victoria, Australia
Optical Motion Technologies
Reduced Vibration by
Diagnosis in Less Than
Savings Per Hour
“This has proved to be a great assistance to rectifying a long-term plant issue. After only a short set up time it confirmed our vibration and phase measurement’s without physically touching the plant.”Peter Fanning, Condition Monitoring Team Leader at AGL Loy Yang
There are two (duty and stand-by) Stator Coolant Pumps (SCP) critical to the operation of each 500+ megawatt turbo generator at the Loy Yang Power Station. One of the two SCPs for Unit 1 turbo generator has had a long history, more than 10 years, of high lateral vibration, sometimes reaching 20 mm/sec RMS. There have been many attempts to remedy the problem at an estimated material cost of AU$160k. This does not take into account the estimated labor cost of 500+ man hours and loss of power generation revenue. Some of the attempts to remedy the problem include: laser alignment, base frame spot welds, bracing of pipework, fitment of flexible bellows to the pump suction and discharge pipework, pump replacement x2, motor replacement, coupling replacement, etc.
Optical Motion Technologies (OMT) were contracted to apply RDI’s Motion Amplification™ (MA) technology to solving the long running problem on 1-SCP-2. From arriving at the location of the SCPs in the power station, setting up the video camera acquisition system and then collecting nine MA videos took less than one hour. This hour included the time to analyze the results all of which was done in the field. The process involved taking wide angle ‘whole of machine’ videos, analyzing them in the field and then honing in with zoomed videos on the root cause of the problem. It was clear from the MA videos that the problem was a soft foot condition between the pump base frame and skid base plate. In fact, there was a twisting operational deflection shape of the pump base frame. During a scheduled outage, a series of fillet welds were made across the suction end the pump base frame to the skid base plate. When the pump was returned to duty service the high lateral motion and vibration had been reduced by more than 70% and was now less than 5 mm/sec RMS. The solution to this problem was achieved through the application of RDI’s Motion Amplification™ technology for a fraction of the time and cost already incurred.
Want to learn more? For more information or a quote on our products please contact us.
To find your license in the software follow the instructions below if you don’t have access to your software you can use this FAQ:
Open the “RDI Motion Amplification” Program
Click on the “Information” icon in the upper right-hand corner
Your license ID is located on this screen identified by the green box